Completed August 2019
Location Poway CA San Diego
There was a gas leak coming from the meter to the house. San Diego Gas and Electric shut off the gas meter. We replaced the entire gas line, inch and half in size, from meter to he house. we trenched approximately 55 feet long and dug the trench to the appropriate depth. Installed new plyetheline gas pipe with tracer wire and proper risers, tested the system for any leaks with compressed air. City inspector came out to the jobsite and passed our work, as everything was done up to code to city standards. After the city inspector passed our gas line, SDG&E came and turned on the gas.